- Energy recovery from waste and biomass technical solutions 889.26 KB
- Understanding the impact of feedstock variation 324.98 KB
- Fluidized bed combustion plant expertise 120.74 KB
- Carbon footprint assessment and management 96.88 KB
- Power plant risk assessment and management 88.05 KB
- Power plant owners engineering 124.29 KB
- Power plant fuel optimization 170.45 KB
- Power plant outage solutions 98.16 KB
- Power plant inspection and outage management 97.39 KB
- Power plant failure root cause analysis 79.96 KB
We offer alternative solutions that are focused on your priorities, helping you to reduce costs and increase your independence from original equipment manufacturers
Stay compliant - ensure your assets comply with environmental regulations
Improve reliability - optimize O&M strategies through asset health and performance monitoring
Reduce expenditure - O&M strategy solutions
Operator experiences and large scale biomass conversions will be the focus for a joint Uniper and TWI workshop
This event will have valuable content for plant operators and engineers, asset managers and project engineers working in the energy from waste and biomass industry. For more details click here or to register, please email firstname.lastname@example.org
Stay up to date with targeted industry insights from Uniper, and receive our latest publications such as case studies and paper presentations – all relevant to your industry. It’s fast and free to sign up today.
Our long history as an owner and operator of waste and biomass generation assets gives us a deep understanding of the key challenges facing plant operators.
Supporting claim against OEM
Our client was concerned that performance of the air-cooled condenser of their recently commissioned waste to energy plant was below design values, potentially reducing maximum power output during the summer period. Our specialist tests determined that the air flow to the ACC was almost 60% below the design value, making a significant impact on steam turbine power output during periods of high ambient temperature. Further measurements confirmed the ACC was not operating at design conditions. Our client was able to use the data in claims against the OEM to provide a ‘fit for purpose’ plant.
Feasibility, Construction, Commissioning
Independent performance assessment
Our client chose us to provide an independent and trusted view of their new equipment’s performance. They needed assurance that the performance tests were conducted correctly and were independent of the original equipment manufacturer (OEM).
Operation & Maintenance
Swift response ensures plant availability
Our client had identified high temperature and vibration readings from a turbine gearbox, inspection and repairs were required at very short notice. Our turbine engineers responded quickly and were on-site to coincide with a planned outage. We worked round-the-clock to carry out repairs of the gearbox. Inspection highlighted the need for additional refurbishment of bearings and couplings.
Asset Management & Optimization
Evaluating proposed investment
Our client needed independent data prior to a proposed boiler redesign at their waste-fired plant. Our reliable and independent data on furnace performance supported the design and evaluation of proposed plant improvements.
Relocation of turbine and generator island
A German client asked us to relocate the turbine, gearbox, generator and oil system of a 34 MWel, 90 MWthermal waste to energy plant to a new location. We decommissioned and dismantled the turbine in its original location, inspected and refurbished all components and installed the turbine on new foundations in the new location. As a result, the turbine and generator island were not only relocated to another plant, we could also increase the process steam pressure and equipped the system with a new control and instrumentation system.